Linear Fresnel reflectors use long assemblies of flat mirrors to focus sunlight onto fixed absorber pipes located above them, thus capable of concentrating sunlight to as high as 30 times of its original intensity (Figures 1 and 2). This concentrated light energy is then converted into thermal energy to heat a fluid in the pipe to a very high temperature. The hot fluid gives off the heat through a heat exchanger to power a steam generator, like in other concentrated solar power plants such as parabolic troughs and power towers.
Compared with parabolic troughs and power towers, linear Fresnel reflectors may be less efficient in generating electricity, but they may be cheaper to build. According to Wikipedia and the National Renewable Energy Laboratory, Fresnel reflectors are the third most used solar thermal technology after parabolic troughs and power towers, with about 15 plants in operation or under construction around the world. To move one small step closer to our goal of providing everyone a one-stop-shop solar modeling software program for solarizing the world, I have added the design, simulation, and analysis capabilities of this type of concentrated solar power technology in Version 7.1.8 of Energy3D.
Like parabolic troughs, Fresnel reflectors are usually aligned in the north-south axis and rotate about the axis during the day for maximal efficiency (interestingly enough, however, some of the current Fresnel plants I found on Google Maps do not stick to this rule — I couldn’t help wondering the rationale behind their design choices). Unlike parabolic troughs, however, the reflectors hardly face the sun directly, as they have to bounce sunlight to the absorber pipe. The reflectors to the east of the absorber start the day with a nearly horizontal orientation and then gradually turn to face west. Conversely, those to the west of the absorber start the day with an angle that faces east and then gradually turn towards the horizontal direction. Due to the cosine efficiency similar to the optics related to heliostats for power towers, the reflectors to the east collect less energy in the morning than in the afternoon and those to the west collect more energy in the morning and less in the afternoon.
Like heliostats for power towers, Fresnel reflectors have both shadowing and blocking losses (Figure 3). Shadowing losses occur when a part of a reflector is shadowed by another. Blocking losses occur when a part of a reflector that receives sunlight cannot reflect the light to the absorber due to the obstruction of another reflector. In addition, Fresnel reflectors suffer from edge losses — the focal line segments of certain portions near the edges may fall out of the absorber tube and their energy be lost, especially when the sun is low in the sky. In the current version of Energy3D, edge losses have not been calculated (they are relatively small compared with shadowing and blocking losses).
Linear Fresnel reflectors can focus light on multiple absorbers. Figure 4 shows a configuration of a compact linear Fresnel reflector with two absorber pipes, positioned to the east and west of the reflector arrays, respectively. With two absorber pipes, the reflectors may be overall closer to the absorbers, but the downside is increased blocking losses for each reflector (Figure 5).